Views: 10 Author: People's Cable Group Co., Ltd. Publish Time: 2021-09-29 Origin: https://www.rmjtcable.com/
The cables used in the low-voltage DC transmission part of the solar photovoltaic power generation system have different requirements for the connection of different components due to different use environments and technical requirements. The overall factors to be considered are: the insulation performance of the cable, the heat-resistant and flame-retardant performance, Engage in aging performance and wire diameter specifications. Specific requirements are as follows:
1. The connecting cable between the solar cell module and the module is generally connected directly with the connecting cable attached to the module junction box. When the length is not enough, a special extension cable can also be used. Depending on the power of the components, this type of connecting cable has three specifications with a cross-sectional area of 2.5m㎡, 4.0m㎡, and 6.0m㎡. This type of connecting cable uses double-layer insulation, which has superior resistance to ultraviolet rays, water, ozone, acid, and salt, as well as superior all-weather capability and abrasion resistance.
2. The connecting cable between the battery and the inverter requires the use of a multi-strand flexible wire that has passed the UL test, and it should be connected as close as possible. Choosing a short and thick cable can reduce the loss of the system, improve efficiency, and enhance reliability.
3. The connecting cables between the battery array and the controller or DC junction box also require the use of multi-strand flexible wires that have passed the UL test. The cross-sectional area specification is determined by the maximum current output of the square array.
The cross-sectional area of the DC cable of each part is determined according to the following principles: The connecting cable between the solar cell module and the module, the connecting cable between the battery and the battery, and the connecting cable of the AC load. Generally, the rated current of the cable selected is the maximum continuous operation of each cable 1.25 times the current; the connecting cable between the solar cell array and the array, the connecting cable between the storage battery (group) and the inverter, the cable rated current is generally 1.5 times of the maximum continuous working current in each cable.
Mob:+86-156 3908 6804
Tel: +86-371-5563 2827
Room 1203, Building 4, East International Plaza, No. 85 Jinshui Road, Zhengdong New Area, Zhengzhou City, Henan Province, Zhengzhou, Henan, China
Copyright © 1987-2020 People’s Cable Group Co.,Ltd.